Ferntree Gully (Victoria) – Colour
2006/7: Ferntree Gully (Victoria) – Colour Apparent 16 HU (Highest Level Only)
2007/8: Ferntree Gully (Victoria) – Colour Apparent 20 HU (Highest Level Only)
2010/11: Ferntree Gully (Victoria) – Colour Apparent 25 HU (Highest Level Only)
Based on aesthetic considerations, true colour in drinking water should not exceed 15 HU.
“… Colour is generally related to organic content, and while colour derived from natural sources such as humic and fulvic acids is not a health consideration, chlorination of such water can produce a variety of chlorinated organic compounds as by-products (see Section 6.3.2 on disinfection by-products). If the colour is high at the time of disinfection, then the water should be checked for disinfection by-products. It should be noted, however, that low colour at the time of disinfection does not necessarily mean that the concentration of disinfection by-products will be low…
Ferntree Gully – Victoria – Turbidity
2008/9: Ferntree Gully (Victoria) – Turbidity 19 NTU (Maximum detection during year)
Chlorine-resistant pathogen reduction: Where filtration alone is used as the water treatment
process to address identified risks from Cryptosporidium and Giardia, it is essential
that filtration is optimised and consequently the target for the turbidity of water leaving
individual filters should be less than 0.2 NTU, and should not exceed 0.5 NTU at any time
Disinfection: A turbidity of less than 1 NTU is desirable at the time of disinfection with
chlorine unless a higher value can be validated in a specific context.
Aesthetic: Based on aesthetic considerations, the turbidity should not exceed 5 NTU at the