Warruwi (Northern Territory) – Aluminium
2016/17: Warruwi Aluminium 1.27mg/L
According to the ADWG, no health guideline has been adopted for Aluminium, but that the issue is still open to review. Aluminium can come from natural geological sources or from the use of aluminium salts as coagulants in water treatment plants. According to the ADWG “A well-operated water filtration plant (even using aluminium as a flocculant) can achieve aluminium concentrations in the finished water of less than 0.1 mg/L.
The most common form of aluminium in water treatment plants is Aluminium Sulfate (Alum). Alum can be supplied as a bulk liquid or in granular form. It is used at water treatment plants as a coagulant to remove turbidity, microorganisms, organic matter and inorganic chemicals. If water is particularly dirty an Alum dose of as high as 500mg/L could occur. There is also concern that other metals may also exist in refined alum.
While the ADWG mentions that there is considerable evidence that Aluminium is neurotoxic and can pass the gut barrier to accumulate in the blood, leading to a condition called encephalopathy (dialysis dementia) and that Aluminium has been associated with Parkinsonism dementia and amyotrophic lateral sclerosis, the NHMRC, whilst also acknowledging studies which have linked Aluminium with Alzheimer disease, has not granted Aluminium a NOEL (No Observable Effect Level) due to insufficient and contradictory data. Without a NOEL, a health guideline cannot be established. The NHMRC has also stated that if new information comes to hand, a health guideline may be established in the future.
In communication with Aluminium expert Dr Chris Exley (Professor in Bioinorganic Chemistry
The Birchall Centre, Lennard-Jones Laboratories, Keele University, Staffordshire UK) in March 2013 regarding high levels of Aluminium detected in the South Western Victorian town of Hamilton
“It is my opinion that any value above 0.5 mg/L is totally unacceptable and a potential health risk. Where such values are maintained over days, weeks or even months, as indeed is indicated by the data you sent to me, these represent a significant health risk to all consumers. While consumers may not experience any short term health effects the result of longer term exposure to elevated levels of aluminium in potable waters may be a significant increase in the body burden of aluminium in these individuals. This artificially increased body burden will not return to ‘normal’ levels when the Al content of the potable water returns to normal but will act as a new platform level from which the Al body burden will continue to increase with age.
Warruwi (Northern Territory) – Sodium
2016/17: Warruwi Sodium 193mg/L
should not exceed 180 mg/L….The sodium ion is widespread in water due to the high solubility of sodium salts and the abundance of mineral deposits. Near coastal areas, windborne sea spray can make an important contribution either by fallout onto land surfaces where it can drain to drinking water sources, or from washout by rain. Apart from saline intrusion and natural contamination, water treatment chemicals, domestic water softeners and
sewage effluent can contribute to the sodium content of drinking water.” ADWG 2011
Warruwi (Northern Territory) Iron
2007/08: Warruwi Iron 0.59mg/L
Based on aesthetic considerations (precipitation of iron from solution and taste),
the concentration of iron in drinking water should not exceed 0.3 mg/L.
No health-based guideline value has been set for iron.
Iron has a taste threshold of about 0.3 mg/L in water, and becomes objectionable above 3 mg/L. High iron concentrations give water an undesirable rust-brown appearance and can cause staining of laundry and plumbing fittings, fouling of ion-exchange softeners, and blockages in irrigation systems. Growths of iron bacteria, which concentrate iron, may cause taste and odour problems and lead to pipe restrictions, blockages and corrosion. ADWG 2011
Warruwi (Northern Territory) – pH (acidic)
2008/09: Warruwi 4.8 pH
2008/09: Warruwi 5.8 pH
2009/10: Warruwi 5.1 pH
2010/11: Warruwi 5.3 pH
2013/14: Warruwi 5.4 pH
2015/16: Warruwi 5.3 pH
2016/17: Warruwi 4.8 pH
Based on the need to reduce corrosion and encrustation in pipes and fittings, the pH of
drinking water should be between 6.5 and 8.5.
New concrete tanks and cement-mortar lined pipes can significantly increase pH and
a value up to 9.2 may be tolerated, provided monitoring indicates no deterioration in
pH is a measure of the hydrogen ion concentration of water. It is measured on a logarithmic scale from 0 to 14. A pH of 7 is neutral, greater than 7 is alkaline, and less than 7 is acidic.
One of the major objectives in controlling pH is to minimise corrosion and encrustation in pipes and fittings. Corrosion can be reduced by the formation of a protective layer of calcium carbonate on the inside of the pipe or fitting, and the formation of this layer is affected by pH, temperature, the availability of calcium (hardness) and carbon dioxide. If the water is too alkaline (above pH 8.5), the rapid deposition and build-up of calcium carbonate that can result may eventually block the pipe.
Warruwi – Northern Territory – Hardness
2016/17: Warruwi Hardness 262mg/L
“To minimise undesirable build‑up of scale in hot water systems, total hardness (as calcium
carbonate) in drinking water should not exceed 200 mg/L.
Hard water requires more soap than soft water to obtain a lather. It can also cause scale to form on hot water pipes and fittings. Hardness is caused primarily by the presence of calcium and magnesium ions, although other cations such as strontium, iron, manganese and barium can also contribute.”
Australian Drinking Water Guidelines 2011
Warruwi – Northern Territory – Total Dissolved Solids
2016/17: Warruwi Total Dissolved Solids 703mg/L
“No specific health guideline value is provided for total dissolved solids (TDS), as there are no
health effects directly attributable to TDS. However for good palatability total dissolved solids
in drinking water should not exceed 600 mg/L.
Total dissolved solids (TDS) consist of inorganic salts and small amounts of organic matter that are dissolved in water. Clay particles, colloidal iron and manganese oxides and silica, fine enough to pass through a 0.45 micron filter membrane can also contribute to total dissolved solids.
Total dissolved solids comprise: sodium, potassium, calcium, magnesium, chloride, sulfate, bicarbonate, carbonate, silica, organic matter, fluoride, iron, manganese, nitrate, nitrite and phosphates…” Australian Drinking Water Guidelines 2011
Warruwi (Northern Territory) – Chloride
2016/17: Warruwi Chloride 416mg/L
“Chloride is present in natural waters from the dissolution of salt deposits, and contamination from effluent disposal. Sodium chloride is widely used in the production of industrial chemicals such as caustic soda, chlorine, and sodium chlorite and hypochlorite. Potassium chloride is used in the production of fertilisers.
The taste threshold of chloride in water is dependent on the associated cation but is in the range 200–300 mg/L. The chloride content of water can affect corrosion of pipes and fittings. It can also affect the solubility of metal ions.
In surface water, the concentration of chloride is usually less than 100 mg/L and frequently below 10 mg/L. Groundwater can have higher concentrations, particularly if there is salt water intrusion.
Based on aesthetic considerations, the chloride concentration in drinking water should not exceed 250 mg/L.
No health-based guideline value is proposed for chloride.” 2011 Australian Drinking Water Guidelines