Kulin (Western Australia) – pH (alkaline)
Average pH: 2007 July-2008 June: 9.17 pH units
Average pH: 2008 July-2009 June: 8.99 pH units
Average pH: 2009 July-2010 June: 8.90 pH units
2010/11 Kulin (Western Australia) pH 9.06 (av)
2011/12 Kulin (Western Australia) pH 9.26 (av)
2013/14 Kulin (Western Australia) pH 9.02 (av)
Based on the need to reduce corrosion and encrustation in pipes and fittings, the pH of
drinking water should be between 6.5 and 8.5.
New concrete tanks and cement-mortar lined pipes can significantly increase pH and
a value up to 9.2 may be tolerated, provided monitoring indicates no deterioration in
pH is a measure of the hydrogen ion concentration of water. It is measured on a logarithmic scale from 0 to 14. A pH of 7 is neutral, greater than 7 is alkaline, and less than 7 is acidic.
One of the major objectives in controlling pH is to minimise corrosion and encrustation in pipes and fittings. Corrosion can be reduced by the formation of a protective layer of calcium carbonate on the inside of the pipe or fitting, and the formation of this layer is affected by pH, temperature, the availability of calcium (hardness) and carbon dioxide. If the water is too alkaline (above pH 8.5), the rapid deposition and build-up of calcium carbonate that can result may eventually block the pipe.