Kununoppin (Western Australia) – Thermophilic Naegleria detection
2008/9: Kununoppin (WA) Thermophilic Naegleria 1/12 samples positive.
“GUIDELINE No guideline value is set for Naegleria fowleri in drinking water, but an ‘action level’ is recommended for water supplies likely to be contaminated. If the organism is detected, advice should be sought from the relevant health authority.
Naegleria fowleri is a free-living, thermophilic amoeboflagellate which causes the waterborne disease primary amoebic meningoencephalitis (PAM). This rare but fatal condition has followed use of water for swimming, or domestic bathing. The organism occurs naturally in freshwater of suitable temperature, feeding on bacteria. Its occurrence is only indirectly related to human activity, inasmuch as such activity may modify temperatures or promote bacterial production. PAM has been reported from many countries, usually associated with thermally polluted environments, geothermal water or heated swimming pools. N. fowleri is almost exclusively aquatic, and water is the only known source of infection. Numerous nonvirulent Naegleria species are known in Australia.
PAM cases have been recorded from South Australia, Western Australia, Queensland and New South Wales; Naegleria fowleri has been detected in water in each of these states and in the Northern Territory. Australia is the only country where N. fowleri has been detected in public water supplies (Dorsch et al. 1983). Most of the available data on the density of N. fowleri in water relates to water supplies in South Australia (including the highest reported densities). In temperate Australia, significant seasonal cycles of density occur, from below one organism per litre to hundreds or thousands per litre in poorly disinfected water (Robinson and Christy 1984). N. fowleri detected at water temperatures below 18°C is likely to be present as cysts, which are not infectious, but which may seed a suitable environment.” Australian Drinking Water Guidelines 2011
Kununoppin (Western Australia) – pH (alkaline)
Average pH: 2007 July-2008 June: 8.81 pH units
Average pH: 2009 July-2010 June: 8.96 pH units
2010/11 Kununoppin (Western Australia) pH 8.75 (av)
2011/12 Kununoppin (Western Australia) pH 8.67 (av)
2015/16 Kununoppin (Western Australia) pH 8.78 (av)
2016/17 Kununoppin (Western Australia) pH 8.55 (av)
2017/18 Kununoppin (Western Australia) pH 8.97 (av)
2019/20: Kununoppin (Western Australia) 8.8pH (av)
Based on the need to reduce corrosion and encrustation in pipes and fittings, the pH of
drinking water should be between 6.5 and 8.5.
New concrete tanks and cement-mortar lined pipes can significantly increase pH and
a value up to 9.2 may be tolerated, provided monitoring indicates no deterioration in
pH is a measure of the hydrogen ion concentration of water. It is measured on a logarithmic scale from 0 to 14. A pH of 7 is neutral, greater than 7 is alkaline, and less than 7 is acidic.
One of the major objectives in controlling pH is to minimise corrosion and encrustation in pipes and fittings. Corrosion can be reduced by the formation of a protective layer of calcium carbonate on the inside of the pipe or fitting, and the formation of this layer is affected by pH, temperature, the availability of calcium (hardness) and carbon dioxide. If the water is too alkaline (above pH 8.5), the rapid deposition and build-up of calcium carbonate that can result may eventually block the pipe.