Ora Banda (Western Australia) – pH (alkaline)
Ora Banda Average pH: 2007 July-2008 June: 8.51 pH units
Ora Banda Average pH: 2009 July-2010 June: 8.63 pH units
2010/11: Ora Banda (Western Australia) pH 8.59 (av)
2011/12 Ora Banda (Western Australia) pH 8.51 (av)
2015/16 Ora Banda (Western Australia) pH 8.55 (av)
2019/20: Ora Banda (Western Australia) 8.51pH (av)
Based on the need to reduce corrosion and encrustation in pipes and fittings, the pH of
drinking water should be between 6.5 and 8.5.
New concrete tanks and cement-mortar lined pipes can significantly increase pH and
a value up to 9.2 may be tolerated, provided monitoring indicates no deterioration in
pH is a measure of the hydrogen ion concentration of water. It is measured on a logarithmic scale from 0 to 14. A pH of 7 is neutral, greater than 7 is alkaline, and less than 7 is acidic.
One of the major objectives in controlling pH is to minimise corrosion and encrustation in pipes and fittings. Corrosion can be reduced by the formation of a protective layer of calcium carbonate on the inside of the pipe or fitting, and the formation of this layer is affected by pH, temperature, the availability of calcium (hardness) and carbon dioxide. If the water is too alkaline (above pH 8.5), the rapid deposition and build-up of calcium carbonate that can result may eventually block the pipe.
2017/18 Ora Banda (Western Australia) – Turbidity
2017/18 Ora Banda (Western Australia) Turbidity 6.6NTU (max), 3.3NTU (mean)
Chlorine-resistant pathogen reduction: Where filtration alone is used as the water treatment
process to address identified risks from Cryptosporidium and Giardia, it is essential
that filtration is optimised and consequently the target for the turbidity of water leaving
individual filters should be less than 0.2 NTU, and should not exceed 0.5 NTU at any time
Disinfection: A turbidity of less than 1 NTU is desirable at the time of disinfection with
chlorine unless a higher value can be validated in a specific context.
Aesthetic: Based on aesthetic considerations, the turbidity should not exceed 5 NTU at the