Thermotolerant coliforms are a sub-group of coliforms that are able to grow at 44.5 ± 0.2°C. E. coli is the most common thermotolerant coliform present in faeces and is regarded as the most specific indicator of recent faecal contamination because generally it is not capable of growth in the environment. In contrast, some other thermotolerant coliforms (including strains of Klebsiella, Citrobacter and Enterobacter) are able to grow in the environment and their presence is not necessarily related to faecal contamination. While tests for thermotolerant coliforms can be simpler than for E. coli, E. coli is considered a superior indicator for detecting faecal contamination…” ADWG
2008/13 Stuarts Point (NSW) – Lead
2008/13 – Stuarts Point (NSW) – Lead 0.022mg/L (max) 0.0014mg/L (mean)
Lead Australian Drinking Water Guideline 0.01mg/L
“… Lead can be present in drinking water as a result of dissolution from natural sources, or from household plumbing systems containing lead. These may include lead in pipes, or in solder used to seal joints. The amount of lead dissolved will depend on a number of factors including pH, water hardness and the standing time of the water.
Lead is the most common of the heavy metals and is mined widely throughout the world. It is used in the production of lead acid batteries, solder, alloys, cable sheathing, paint pigments, rust inhibitors, ammunition, glazes and plastic stabilisers. The organo-lead compounds tetramethyl and tetraethyl lead are used extensively as anti-knock and lubricating compounds in gasoline…ADWG 2011
2008/13 Stuarts Point (NSW) – Iron
2008/13 – Stuarts Point (NSW) – Iron 2.79mg/L (max), 0.21mg/L (mean)
From a total of 246 samples, 5 exceedances occurred from 1 Jan 2004 to 31 Mar 2014. The ADWG value for iron based on aesthetic considerations is 0.3 mg/L.
Based on aesthetic considerations (precipitation of iron from solution and taste),
the concentration of iron in drinking water should not exceed 0.3 mg/L.
No health-based guideline value has been set for iron.
Iron has a taste threshold of about 0.3 mg/L in water, and becomes objectionable above 3 mg/L. High iron concentrations give water an undesirable rust-brown appearance and can cause staining of laundry and plumbing fittings, fouling of ion-exchange softeners, and blockages in irrigation systems. Growths of iron bacteria, which concentrate iron, may cause taste and odour problems and lead to pipe restrictions, blockages and corrosion. ADWG 2011
2008/13 – Stuarts Point (New South Wales) – Arsenic
2008/13: Stuarts Point Arsenic 0.03mg/L (max), 0.0026mg/L (mean)
Arsenic: Australian Drinking Water Guideline = 0.01mg/L
Arsenic is bioaccumulative and symptoms may take 10-15 years to develop after expsoure at high levels. Drinking water can be contaminated with inorganic arsenic through wind blown dust, leaching or runoff from soil, rocks and sediment. Groundwater sources such as bores will usually have higher arsenic levels than surface water. In major Australian reticulated water supplies concentrations of arsenic range up to 0.015mg/L, with typical values less than
2008/13 – Stuarts Point (New South Wales) – Turbidity
2008/13: Stuarts Point (New South Wales) Turbidity 9.73NTU (max), 0.63 NTU (mean)
Chlorine-resistant pathogen reduction: Where filtration alone is used as the water treatment
process to address identified risks from Cryptosporidium and Giardia, it is essential
that filtration is optimised and consequently the target for the turbidity of water leaving
individual filters should be less than 0.2 NTU, and should not exceed 0.5 NTU at any time
Disinfection: A turbidity of less than 1 NTU is desirable at the time of disinfection with
chlorine unless a higher value can be validated in a specific context.
Aesthetic: Based on aesthetic considerations, the turbidity should not exceed 5 NTU at the