(Central Highlands Water Annual Drinking Water Quality Report 2008-9)
18 December 2008 – Ballarat Road Basin, Creswick (Ballarat System) E.coli 1org/100mL. Inspection of tank and resample. No E. coli detected in resample. Informed DHS of inital resample results. (Central Highlands Water Annual Drinking Water Quality Report 2008-9)
9 November 2011 (6 days) Ballarat Road Basin, Creswick (Ballarat System) E. coli – 18 org/100mL Creswick Reticulation (Ballarat System)
“Coliforms are Gram-negative, non-spore-forming, rod-shaped bacteria that are capable of aerobic and facultative anaerobic growth in the presence of bile salts or other surface active agents with similar growth-inhibiting properties. They are found in large numbers in the faeces of humans and other warm-blooded animals, but many species also occur in the environment.
Thermotolerant coliforms are a sub-group of coliforms that are able to grow at 44.5 ± 0.2°C. E. coli is the most common thermotolerant coliform present in faeces and is regarded as the most specific indicator of recent faecal contamination because generally it is not capable of growth in the environment. In contrast, some other thermotolerant coliforms (including strains of Klebsiella, Citrobacter and Enterobacter) are able to grow in the environment and their presence is not necessarily related to faecal contamination. While tests for thermotolerant coliforms can be simpler than for E. coli, E. coli is considered a superior indicator for detecting faecal contamination…” ADWG 2011
2012/17 – Creswick Victoria) – Turbidity (highest levels)
2012/13 Creswick Turbidity 8.9NTU
2016/17Creswick Turbidity 10NTU
Chlorine-resistant pathogen reduction: Where filtration alone is used as the water treatment
process to address identified risks from Cryptosporidium and Giardia, it is essential
that filtration is optimised and consequently the target for the turbidity of water leaving
individual filters should be less than 0.2 NTU, and should not exceed 0.5 NTU at any time
Disinfection: A turbidity of less than 1 NTU is desirable at the time of disinfection with
chlorine unless a higher value can be validated in a specific context.
Aesthetic: Based on aesthetic considerations, the turbidity should not exceed 5 NTU at the