11/9/14 – Esk WTP (Queensland) – E.coli
Esk WTP (E.coli 2 MPN/100 mL, 10/09/2014. Seqwater confirmed that there were no operational issues at Esk WTP and that disinfection was within specification. There was chlorine residual at the time of sampling of 2.3 mg/L. Resampling and testing occurred to confirm that there were no issues. The downstream distribution entity confirmed that they had no detections and that chlorine residuals were at normal levels in the distribution system.
SEQWater Annual Drinking Water Quality Plan 2015/16
“Coliforms are Gram-negative, non-spore-forming, rod-shaped bacteria that are capable of aerobic and facultative anaerobic growth in the presence of bile salts or other surface active agents with similar growth-inhibiting properties. They are found in large numbers in the faeces of humans and other warm-blooded animals, but many species also occur in the environment.
Thermotolerant coliforms are a sub-group of coliforms that are able to grow at 44.5 ± 0.2°C. E. coli is the most common thermotolerant coliform present in faeces and is regarded as the most specific indicator of recent faecal contamination because generally it is not capable of growth in the environment. In contrast, some other thermotolerant coliforms (including strains of Klebsiella, Citrobacter and Enterobacter) are able to grow in the environment and their presence is not necessarily related to faecal contamination. While tests for thermotolerant coliforms can be simpler than for E. coli, E. coli is considered a superior indicator for detecting faecal contamination…” ADWG
Esk – Queensland – Temperature
2016/17: Esk (Queensland) – Temperature 25C
“No guideline is set due to the impracticality of controlling water temperature.
Drinking water temperatures above 20°C may result in an increase in the number of
Temperature is primarily an aesthetic criterion for drinking water. Generally, cool water is more palatable than warm or cold water. In general, consumers will react to a change in water temperature. Complaints are most frequent when the temperature suddenly increases.
The turbidity and colour of filtered water may be indirectly affected by temperature, as low water temperatures tend to decrease the efficiency of water treatment processes by, for instance, affecting floc formation rates and sedimentation efficiency.
Chemical reaction rates increase with temperature, and this can lead to greater corrosion of pipes and fittings in closed systems. Scale formation in hard waters will also be greater at higher temperatures…
Water temperatures in major Australian reticulated supplies range from 10°C to 30°C. In some long, above-ground pipelines, water temperatures up to 45°C may be experienced…
The effectiveness of chlorine as a disinfectant is influenced by the temperature of the water being dosed. Generally higher temperatures result in more effective disinfection at a particular chlorine dose, but this may be counterbalanced by a more rapid loss of chlorine to the atmosphere (AWWA 1990).