St Marys (Tasmania) – Turbidity
2017/18: St Marys (Tasmania) – Turbidity 12.4 NTU (Max), 1.19 NTU (mean)
Chlorine-resistant pathogen reduction: Where filtration alone is used as the water treatment
process to address identified risks from Cryptosporidium and Giardia, it is essential
that filtration is optimised and consequently the target for the turbidity of water leaving
individual filters should be less than 0.2 NTU, and should not exceed 0.5 NTU at any time
Disinfection: A turbidity of less than 1 NTU is desirable at the time of disinfection with
chlorine unless a higher value can be validated in a specific context.
Aesthetic: Based on aesthetic considerations, the turbidity should not exceed 5 NTU at the
St Marys – Tasmania – Temperature
January 19 2016: St Marys (Tasmania) – Temperature 21.4C
February 9 2016: St Marys (Tasmania) – Temperature 21.8C
March 8 2016: St Marys (Tasmania) – Temperature 21.4C
“No guideline is set due to the impracticality of controlling water temperature.
Drinking water temperatures above 20°C may result in an increase in the number of
Temperature is primarily an aesthetic criterion for drinking water. Generally, cool water is more palatable than warm or cold water. In general, consumers will react to a change in water temperature. Complaints are most frequent when the temperature suddenly increases.
The turbidity and colour of filtered water may be indirectly affected by temperature, as low water temperatures tend to decrease the efficiency of water treatment processes by, for instance, affecting floc formation rates and sedimentation efficiency.
Chemical reaction rates increase with temperature, and this can lead to greater corrosion of pipes and fittings in closed systems. Scale formation in hard waters will also be greater at higher temperatures…
Water temperatures in major Australian reticulated supplies range from 10°C to 30°C. In some long, above-ground pipelines, water temperatures up to 45°C may be experienced…
The effectiveness of chlorine as a disinfectant is influenced by the temperature of the water being dosed. Generally higher temperatures result in more effective disinfection at a particular chlorine dose, but this may be counterbalanced by a more rapid loss of chlorine to the atmosphere (AWWA 1990).