Yunyarinyi (South Australia) – Fluoride
15 August 2016: Yunyarinyi (South Australia) – Fluoride 1.6mg/L
“Fluoride occurs naturally in seawater (1.4 mg/L), soil (up to 300 parts per million) and air (from volcanic gases and industrial pollution). Naturally occurring fluoride concentrations in drinking water depend on the type of soil and rock through which the water drains. Generally, concentrations in surface water are relatively low (<0.1–0.5 mg/L), while water from deeper wells may have quite high concentrations (1–10 mg/L) if the rock formations are fluoride-rich.” 2011 ADWG. Health Guideline: 1.5mg/L
Yunyarinyi (South Australia) – Silica
19 August 2013: Yunyarinyi (South Australia). Silica 82mg/L
5 August 2014: Yunyarinyi (South Australia). Silica 78.9mg/L
To minimise an undesirable scale build up on surfaces, silica (SiO2) within drinking waters should not exceed 80 mg/L.
Silica present in water is usually referred to as amorphous silica (i.e. lacking any crystalline structure). When silica is dissolved within water it forms monosilicic acid:
SiO2 + 2H2O à Si(OH)4
When the concentrations of monosilicic acid increase, polymerisation of the silica occurs, forming polysilicic acids followed by formation of colloidal silica. Monosilicic acid and polysilicic acids are the forms of silica analysed when determining dissolved silica content.
The deposition of silica from solutions can occur via various mechanisms. The deposition of silica that can cause the most problems for the water industry is via silica’s ability to deposit on solid surfaces that have hydroxyl (OH) groups present. Surfaces that commonly have hydroxyl groups present are glass and metallic surfaces. For example, dissolved silica will react with the surfaces of glass and begin to form a white precipitate. The silica forms silicates on the surface, resulting in silica build-up. In cases where customer complaints occur due to scale build-up, water hardness and silica concentrations should be investigated to determine the cause.
Silica can be a problem in water treatment due to its ability to cause fouling of reverse osmosis (RO) membranes (Sheikholeslami and Tan, 1999, Ning 2002, Sahachaiyunta and Sheikholeslami 2002). This occurs when the dissolved silica of the concentrate becomes super-saturated, causing silicates to form in the presence of metals, and these deposit on the membrane surface. The silicate then dehydrates, forming hard layers on the membrane that reduce the effectiveness of the process… 2011 ADWG
2012/16 – Yunyarinyi (South Australia) – Hardness
2012/16: Yunyarinyi (South Australia) – Hardness average 254.4mg/L (5 detections out of 5 above guideline)
“To minimise undesirable build‑up of scale in hot water systems, total hardness (as calcium
carbonate) in drinking water should not exceed 200 mg/L.
Hard water requires more soap than soft water to obtain a lather. It can also cause scale to form on hot water pipes and fittings. Hardness is caused primarily by the presence of calcium and magnesium ions, although other cations such as strontium, iron, manganese and barium can also contribute.”